Here we installed a Worcester 18i system boiler with an internal diverter kit so that the boiler can recharge the hot water cylinder at full rate then return to heating the radiator system using compensating controls.
This powermax had done it's job well and it was time for an upgrade. We replaced it with a Worcester Bosch Life combination boiler but as you can see it was located in an internal cupboard so we used a high level horizontal flue kit and 3/4 ply to add strength and support to the metal frame internal wall. This customer used the Bosch easy smart thermostat to control the heating from anywhere.
Worcester 8000 Life installation carried out run Pontllanfraith, along with the new brass filter and load compensating controls.
Here we replaced an old floor standing boiler with the new Worcester 8000 Life combination boiler along with a full heated power flush, weather and load compensating controls built into the smart thermostat.
Here was replaced a Baxi Bermuda back boiler and gravity hot water system and replaced it with the new Worcester 2000 30kw combination boiler. The heating was range rated down to 15kw. This boiler comes with a 6 year parts and labour guarantee and wireless load compensating controls as standard.
Here we replaced a Ferroli combi with the new Worcester Bosch 8000 Life 30kw Combi. The 8000 series has 10:1 modulation meaning it can modulate the burner output down to 3kw, this reduces cycling (on and off) of the boiler which in turn increases the efficiency by being able to condense for longer periods of time whilst reducing the stress on the whole system.
Here we replaced a prismatic cylinder feeding a back boiler in the lounge with a Worcester Bosch 29CDi Classic Combi. We used the Worcester comfort RF2 load compensating room thermostat to control the flow temperature to the heating system. This control system monitors the internal room temperature against the target temperature to provide efficiency whilst maintaining comfort. We've used a spirotech Rv2 deaerator to remove micro bubbles from the system which helps reduce corrosion, a Hotun Hiflo S.F to combine the pressure relief valve with the condensate and a Worcester Greenstar system filter to collect any remaining magnetite (sludge) from the system after the powerflush.
This homeowner took it upon themselves to reduce the amount of fossil fuels they burn by choosing a solar thermal heating system. This system has the potential to provide them with upto 60% of the annual hot water demand. This Worcester Bosch system comes with a 10 year parts and labour guarantee.
Job that we carried out in Cwmfelinfach, replacing a 40 year old floor standing boiler and gravity hot water system to a Worcester Bosch Grecnstar 30i combination boiler.
Here we swapped a Sime combination boiler for a Worcester Bosch 29 CDi condensing combination boiler.
Other images are of a thermal camera shot once we had carried out a magnacleanse flush of the system, you can see the radiator warming up with no issues. The other is a photo our prime lab kit with the iron level results in the system.
Here we replace a Baxi Bermuda back boiler with a Worcester Bosch Greenstar 30i in Newbridge. We also repiped the whole house and installed new radiators.
Here we are carrying out a heated powerflush as part of a new boiler installation. We flush out the heating system prior to commission the new boiler, don't want dirty water going through a new boiler!
Here we was asked to take part in a chapel renovation in Abercarn. We installed a Worcester Bosch 35 CDi system boiler with integral diverter and a 210 litre Worcester Greenstore unvented hot water cylinder. The chapel had a total of 20 radiators split over two floors and exceeded the maximum flow rate of the boiler so the slim black box beneath the boiler is the Worcester low loss header. This separates the boiler from the system giving us the ability to overcome the flow rate problem.